Horizontal Air Handling Units Ductable Fan Coil Units
|Model||AC+WSP 2 ÷ 40|
|Supply ability||1000 sets per month|
|Payment||50% T/T as deposit rest before delivery|
|Packaging||Export Standard Package|
This series ductable fan coil units are designed in 3 types installation: vertical, horizontal and ceiling mounted, to meet the varied requirements of zone cooling or heating using chilled water or hot water, suitable for cooling/heating, dehumidifying of air conditioning environment. This range is widely used in industrial and commercial buildings, such as shopping centre, textile factories, electronic factories and hospitals where need air treatment.
Air handling units The structure is made with galvanized steel, and aluminum profiles for ceiling mounted type. Pre-painted double-shell steel panels (sandwich type) internally insulated with polyurethane material.
Ductable fan coil units The coils are made of seamless tubes expanded into aluminum fins in continuous block. All coils are tested for leakage.
Big fan coil units External rotor type centrifugal fan motor for vertical and horizontal units, and belt-drive type for ceiling mounted units, low noise.
Air handler units The fan decks are composed of double suction centrifugal fans with aluminum impellers and 3-speed fan motors. Each fan motor assembly is dynamically balanced.
AHU The easily removable filter is made of filtering honeycomb polypropylene fabric and supported by an aluminum frame. Three types pull-out method: up, left and right as request.
Horizontal air handling units The drip trays are made from sheet metal treated with polyester powder coating to ensure total resistance to atmospheric agents.
ELECTRICAL CONNECTION BOX
All electric wires are connected to enclosed electrical terminal block.
l Additional heating coil
l Additional electric heater
l Wet deck type humidifier
l Spray type humidifier (air washer)
l Steam humidifier
GENERAL TECHNICAL DATA
* Sound pressure measured in anechoic room1.5 maway from the unit.
** The data are referred to the following conditions:
l Return air conditions:
Cooling: air intake temperature: DB 27 ºC WB 19.5 ºC, water inlet /outlet temperature: 7/12 ºC.
Heating: air intake temperature: DB 21 ºC, water inlet temperature: 60 ºC.
l Fresh air conditions:
Cooling: air intake temperature: DB 35 ºC WB 28 ºC, water inlet /outlet temperature: 7/12 ºC.
ESP and POWER DATA
Mod.AC+ WSP 2÷40
Air Handling Units/Horizontal Ductable Fan Coil Units/Duct Air Handler Units/AHU
AC+WSP 2 ÷ 40
from 2000 to